A connection to a public water main for a water service line is much more important than a property owner may realize. There can be various issues with a wet tap connection for a service line that will affect the service life of the water line and water pressure for the property:
- A wet tap connection for a main water line may be a ‘driven’. Which means it was installed before power tools were used. A driven tap can blow out of the main line without warning.
- A wet tap connection can be too small to supply the proper volume of water to a property.
- A wet tap connection can leak or be defective.
A driven tap
Driven taps are no longer legal in NYC for a water service line. However an existing wet tap connection will not be violated unless a water main repair or replacement is being performed on that particular water line. Whenever a water main repair or water main replacement is performed and a driven tap is found it must be replaced. Driven taps were installed prior to power tools being utilized by the NYC DEP. They were actually driven into the city water main using a hammer. There are no threads to hold a driven wet tap connection in place and they are prone to blow out. In addition they are typically too small to properly service a property.
An inadequately sized wet tap connection
Many NYC properties have added plumbing fixtures or living space to an existing building over the years. A tap that may have been adequate or marginal years ago will now not provide an adequate volume of water and result in low water pressure as well. Water pressure and volume of water are two separate and distinct issues. No matter how large the actual size of the water service line, if the tap is too small there will not be enough water volume or pressure to property serve the property. The minimum sized wet tap connection allowed for a service line in NYC is 5/8″ for a one family house. Many older taps in NYC are only 1/2″ and wholly inadequate.
A leaking tap
On very rare occasions a tap on a NYC water main may leak or become defective. Sometimes the ‘core’ of the fitting can be tightened, or the connection itself can be screwed further into the NYC water main to stop the leak. But in most cases it would have to be plugged or removed with a new one installed in its place.
An important point:
A brand new properly sized tap installed by the NYC DEP into the city water main costs around $300.00. In almost all cases where low water pressure exists or there’s a chance of a defect it is good policy to replace it for the relatively modest expense of $300.00.
The expertise of the NYC DEP
The NYC DEP has highly experienced crews specializing in wet tap installations. The DEP can do a complete installation for a water service line in about 20 minutes with a total about a 1/2 gallon of water lost during each installation. Furthermore DEP has crews that install many taps each and every day in all five Boroughs to keep NYC water supply lines up to date and up to code.
Only Licensed Master Plumbers can request a connection or an inspection from the DEP, and only after proper permits have been secured. In some cases, such as in an emergency, the DEP will allow for a tap to be installed or grant an inspection – but proper documentation of the situation must be provided by the licensed plumber.
This article was written by David Balkan and is the sole property of Joseph L. Balkan Inc.
Joseph L. Balkan, Inc. | Sewer and Water Main Specialists
130-01 Jamaica Avenue Richmond Hill, NY 11418
Phone: (718) 849-0900 | Espanol (718) 943-5720 | Fax: (718) 849-9570